The Honeywell UDC Universal Digital Controller is a microprocessor-based stand alone controller. It combines the highest degree of functionality and. Find great deals for Honeywell UDC Universal Digital Controller. Shop with confidence on eBay!. There are UDC ‘s at both ends, however as the set point is managed by Lookout, the controllers just provide local control and display the.
|Published (Last):||7 April 2014|
|PDF File Size:||5.55 Mb|
|ePub File Size:||9.87 Mb|
|Price:||Free* [*Free Regsitration Required]|
Since the two can be connected through Lookout, you may consider implementing a staged control wherein the downstream UDC handles a majority of level changes in the reservoir small deviations in level.
Once you verify everything going in and out of the controller as it should I would then start to look at honeuwell INSIDE the controller. By Bill Clemons on 15 July, – 5: You must be a Control.
The lake receives water from a river and releases it to the same honeywlel stream. Could this be a span problem? Use double quotes around phrases, as follows: Open the gate x amount for x period. Please log in and try again.
I would verify your getting a good input signal and the full range of gate movement in reponse. NandaKumar on 16 July, – 8: Since both UDC work to maintain level, there may be conditions where the two work together or against each other to maintain the reservoir level. Perhaps you could order one from Honeywell. Some tips for better search results Inlet Flow and Outlet Flow.
Select the categories for which you would like to see messages displayed Your subscription request is being processed. First mention your complete model no. By Patti on 4 November, – 2: Note that common words and, that, etc. Adjust the head gate position to maintain reservoir level.
I would like a little more clarification on what your measuring and what your controlling – ‘gate position’ is pretty hard to measure unless you have some sort of valve positioner arrangement. By Steve Smoker on 4 October, – 7: I’ve fiddled around with a few UDCs and being typical Honeywell the book is about as clear and thick as mud. To search the site, enter your search terms in the box labeled “search the site” and hit Enter. Username Password Remember me on this computer.
Welcome to the Modbus Community, about the world’s leading automation protocol.
Honeywell UDC – In Stock, We Buy Sell Repair, Price Quote
The UDC configuration described is a level control wherein the object of the control loop appears to be: SPHiLim is the parameter that determines how high the setpoint on the controller can be wound up to.
This control occurs at two places on the reservoir: The UDC configuration described is a level honeywll wherein the object of the control loop appears to be:. If you’re not already a member, consider joining. By Anonymous on 23 July, – You have clicked on the “? Please read those terms and conditions carefully.
Thanks for the reply. It doesnt limit the controller output as the PID function will wind the output up until saturation if the measured value never reaches the setpoint. Try those and reply if its still not working. Hi Patti The bound manual you are looking for is Product E.
Honeywell UDC3000 Specification
The set point should be the desired level of the reservoir. The outlet control is likely configured for direct operation increased level increase output, open gate.
You have given some good problem definition.
The output signal goes to the head gate and adjusts its position to increase or decrease flow into or out of the reservoir. By Chris Jenerick on 14 November, – So that i can help you to resolve the problem.